The technology in the cistern
Pre-assembled components, digitally controllable.
- Max. Water pressure: 10 bar (1 MPa)
- Minimum flow pressure: 1 bar (0,1 MPa)
- Calculation flow: 5 l/min
A dynamic flow valve ensures an operating range of 1 to 10 bar with a constant volume flow of 5 l/min. The corresponding programmed flush volume is thus drained over the calculated flush time.
- 2-pin plug for 12 V power supply
- 5-pin plug for optional connection of building control technology
- All components can be inspected via the flush plate
Programme the TECE hygiene flush with ease
Choose between the “Weekdays” and “Interval” flush programmes.
The interval and flush volume can be continuously adjusted. The interval timer is reset and restarted after a normal water removal.
You can select days and times for flushing. The flush volume can be continuously adjusted here, too. In case of regular water usage, the automatic flush planned for that day is skipped.
The flush volumes for hot and cold water can be set to the individual line volumes independent of one another on each device..
Every piping system has room for reliability and hygiene
Example – Public/semi-public buildings: Looped series installation in a multi-toilet system
To ensure that the total pipe contents up to the riser can be exchanged on an automatic flush, the TECEprofil toilet module with integrated hygiene flush is assigned as the last consumer in the potable water installation. Thanks to the continuously adjustable flush volume, you can also exchange larger pipe volumes, for example in a public toilet with multiple consumers. The “Interval” flush programme is suitable for use in public and semi-public areas to prevent even short usage interruptions.
Example – Hotel: Bathroom installation with dual washstand and looped serial installation.
To ensure that the total pipe contents up to the riser can be exchanged on an automatic flush, the TECEprofil toilet module with integrated hygiene flush is assigned as the last consumer in the potable water installation. Hotel guests in occupied rooms shouldn't be disturbed by an automatic hygiene flush. The “Weekdays” programme helps here. In this programme you can set the flush time for when there are normally no guests in the rooms (e.g. 11:30).